Home | Contact us
This case was initiated by a turbine trip and loss of all feedwater. The pressurizer spray, steam dump and RCP’s are lost on assumption of loss of offsite power. The peak RCS pressure from PCTRAN run did not reach the set point of the pressurizer safety valves (2500 psig). Other than that, everything is pretty agreeable with the Design Document.